Generator Settings on the Sunny Island for Off-Grid Systems
The SMA Sunny Island is a grid-forming battery inverter that can be used for the construction of stand-alone power supply systems. The Sunny Island inverters are capable of forming an AC grid, this sine wave can be used as an interface for PV inverters to synchronize and feed power into the system which is used for supplying loads and recharging batteries.
Off-grid systems can be designed for supplying the complete load, but in order to do so, maximum load and unfavorable weather conditions are to be considered. When designing under these circumstances, the necessary PV system and battery capacity becomes very large which can result in a significant investment.
For the purpose of keeping the system size smaller and therefore reducing the necessary investment, an external AC power source such as a diesel generator set can be used, so that the system can make use of it during periods in which available power is not sufficient for feeding the loads. The generator is also used to supply power to charge the batteries in the case the battery State of Charge (SOC) drops too low.
Here we will be discussing how a generator can be connected to the Sunny Island, the parameters and the settings available for the generator.
Download the white paper for free
Generator and Wiring Requirements:
The generator used must be able to provide a stable grid; typical nominal values are 230V at 50Hz. For a three phase Sunny Island system, a three phase generator will be required. When wiring the generator connections, please ensure that the installation complies with local codes and regulations.
For more details regarding generator compatibility, please refer to the Sunny Island Generator – White Paper, which can be downloaded here.
Connecting the generator to a Single Phase System
The generator must be connected to the AC2 terminal block. In the wiring diagram below, the L, N, and PE are used. The NTT is not used here in the AC2 terminal for an off-grid system.
Circuitry Overview: Single System
Connecting the generator to a Single Phase Single Cluster System
In a single phase operation with multiple Sunny Islands i.e. one, two or three phase setup, the generator connections need to be paralleled to the second and third Sunny Island in order to get power from the generator of approximately 11.5kW per Sunny Island. In single—phase single-cluster systems, the Sunny Island inverters must be of device type SI6.0H-11 or SI8.0H-11.
Circuitry Overview: Single-phase Single-cluster System
Connecting the generator to a Three Phase System
For the three phase setup, each phase is connected directly to the corresponding Sunny Island, where phase 1 is connected to the master unit, phase 2 is connected to slave 1 and phase 3 is connected to slave 2.
Circuitry Overview: Three-phase Single-cluster System
Generator Auto Start Function
The Sunny Island can request the generator to automatically use the built-in relay. To use this function, the generator must support the automatic startup functions. The two signal wires from the generator are connected directly to the built-in relay of the Sunny Island. An example of this wiring is given below.
Setup during commissioning
During the Quick Configuration process done through the Sunny Remote Control (SRC-20), the external source must be set to “Gen”.
The system at this stage should be operational without any further settings and will work based on the default parameters (generator nominal current greater than 16A or approximately 4KVA **). However, some useful settings can be used to fine tune the system.
Settings and Parameters for Installers and Expert Users:
Although the default settings should be enough to run the system, fine tuning the generator parameters will ensure that the system utilizes the generator more efficiently when required. The Sunny Island may need to be in standby mode while this process is being administered and Expert access will be required to access certain parameters. The following settings below can be used to fine tune the generator parameters:
The relay 1 and 2 of the Sunny Island can be used for the generator request. Generally, relay 1 is used for the generator control, and the second relay can be used for the other features and controls such as load shedding functions etc.
By default the relay 1 in set to “AutoGn”.
The settings of the generator can be found in ‘#234 Gen Control.’ The voltage and frequency operating range can be set under these settings. Current drawn from the generator is another major factor, by default the max generator current is set to 16A per Sunny Island. The value can be changed based on the generator rating up to 50A per Sunny Island inverter.
**If the generator’s nominal output current is less than 16A, this parameter must be changed to match the generator’s nominal current to prevent overloading the generator.
Generator warm up time can also be changed. By default it is set at 60s. Please check the generator’s manufacturer recommendations to adjust this timer if required.
One other important parameter is the generator reverse power. The generator manufacturer will provide the maximum reverse current that the generator can handle and the time it is able to withstand the reverse power. By default it is set to 100Watts for 30 sec.
The setting under this menu determines the conditions to start/stop the generator by the Sunny Island.
The most common settings will be the SOC (State Of Charge) values for generator request. By default the lower SOC is 40% and the higher SOC is 80%. What it means is that the Sunny Island will call the generator by activating the relay once the SOC drops to 40%, and will start charging the batteries from the generator power. The cycle completes by stopping the generator once the SOC reaches 80%.
There is also an option for a time dependent generator request with different SOC values for a 24 hour period in this menu.
Another option is the load dependent generator request. This setting can be used to call the generator when the load consumption exceeds the power rating of the Sunny Island. Setting this feature will ensure that the system will be able to function normally even if there is some unexpected load in the system especially at night time.
Once all the settings and parameters are set, under menu #540, the option can be used to turn on the generator manually by setting the parameter to “Start”. Once the relay activates, the generator will start, and once it is able to form a stable grid, the Sunny Island will then be able to sync to it and start drawing power from the generator.
After the test is completed, the parameter must be set to “Auto” for the automatic generator request feature.
In situations when the PV output power is not sufficient to support the loads or there is a low SOC on the batteries, connecting the generator to the Sunny Island will ensure that the extra power is available to fulfill the consumption/demand. Fine tuning the generator will make the off-grid system more robust and will ensure a smooth transition to the generator grid when extra power is required.
Free System Design! Call 720-432-6433
Click ABOVE to enlarge
Click BELOW to browse
Free system design.
Send any questions.
MidNite Solar pre-wired inverter systems offer a turn key solution to installing a battery based inverter system, saving time in the field. With a pre-wired solution all of the confusion is taken out of selecting all the right parts. Hookup between inverters done with included wire and conduit. This system uses 4 of the SMA Sunny Island inverters that are rated at 6,000 watts each and uses a 48 volt battery. It is specifically designed for AC coupling Grid Tie inverters. It works with up to 24KW of grid tie inverters. It produces 120/240 volts AC and has a single AC input.
4 - SMA Sunny Islands Pre-Wired 6048s 120/240 vac Inverters for Off Grid or Battery based Grid tie
4 - MNE250SMA E-Panels
1 - AC Bypass Assembly 120 amp 120/240 vac
2 - MNSPD300’s (Surge Protection Devices)
4 - 250 amp Battery Main Breakers for the Sunny Islands
General labor for assembly, test and crating included
Truck Freight Only
starting from $29,887.98
Free solar + battery system design
Installer network across the USA
Free installation support
Lifetime technical support
Iron Edison is owned and operated by Brandon and Maggie Williams. They have three children, and live and work in Colorado.
Brandon and Maggie believe in energy independence and for the past 10 years they have helped thousands of people achieve their goal of powering their homes with batteries and solar. We love working everyday with our customers and we hope you decide to choose Iron Edison for your battery and solar needs.
Copyright © 2013 Iron Edison, LLC · All rights reserved.Iron Edison
- Kaiser permanente ob gyn appointment
- San francisco restaurant reopening guidelines
- Increased shiny rate pokemon go
- React table custom cell
SMA Sunny Island 6048-US Inverter
SMA Sunny Island 6048-US Inverter/Charger
The ideal solar system battery backup inverter for off-grid power
On-Grid Backup or Off-Grid Power
The Sunny Island inverters are ideal for off-grid battery based solar systems and the best choice for integrating grid-tied battery backup with an existing Sunny Boy grid-tied solar system.
Use the 6048-US with any grid-tied system for on-grid battery backup or off-grid AC power.
The SMA Sunny Island 6048-US inverter is based on the proven off-grid technology in the Sunny Island 5048-US but now features 20 percent more power output. A maximum efficiency of 96 percent ensures peak production, which results in reduced diesel usage and makes a smaller dimensioning of the PV array possible. With Multicluster technology, up to 12 Sunny Islands can be integrated into off-grid power systems up 100 kW in size.
For Grid Connected Applications
The Sunny Island can be added to any existing grid-tie system or even for backup power during power outages. Normally, a grid-tied inverter will shut off during a power outage, leaving you without power. With a complete Sunny Island system, the grid-tie inverter supplies AC power from a solar panel array to charge a battery bank. The Sunny Island reliably supplies power for loads and intelligently monitors and charges battery banks with the energy from local AC sources such as solar, wind or gensets connected on the AC side.
For Off-Grid Remote or Island Power Applications
Featuring sophisticated generator management and true battery state of charge control, the Sunny Island can control a diesel generator connected to it in an extremely fuel efficient manner.
The SI6048-US inverter can be integrated into a public grid or island power grid. This grid can be connected by solar microgrids powered by Sunny Boy PV inverters that are distributed anywhere along the AC grid.
The Sunny Island can be programmed to deactivate loads automatically if the battery is unable to provide sufficient power. This reduces risk of damage to the battery bank.
The redundant design of SMA's AC and DC coupling technology, and expandability of the Sunny Island based solar systems assures the highest reliability and flexibility.
Sunny Island inverters are robust hard-working inverters yet are also designed for regular partial load operation. The Sunny Island has extremely low open-circuit and standby consumption which results in longer battery life, smaller required solar panel array size and reduced diesel usage in rural communities.
Call toll-free (877) 297-0014 for low wholesale prices and expert advice.
We are an Authorized SMA America Supplier.
Seregin's palm covered his penis and squeezed it with force. I suddenly realized that I could finish right now. The pleasure was so strong, and the desire seethed in me for so long that a wave of familiar tickling fullness. Began to rise up the trunk.
Grid system island off sunny
The two of them without saying goodbye to anyone and took a taxi to him. He lived just in general on the other side of the city. On the way I felt bad and ashamed to admit I vomited so much that I barely had time to jump.Sunny Island by SMA
And just a month ago, I once again came to my grandmother. As usual, half-naked, only in shorts he was busy with the housekeeping. Nail it there, fix it there. Summer, heat. I worked in the garden, just opposite Irka's house (since our site is fenced with a grid, the road is clearly visible, but when there is a lot of greenery, I.
- 2007 bmw 328i brake fluid
- 2 inch thick wood shelf
- Uniden bearcat sds100 police scanner
- Toy story 3 game play
- Carmax auto auction run list
- 2015 lexus is 300 horsepower
- Directv christmas movie schedule 2020
- Cheats for sims freeplay lp
- Bluebeam revu alternative for mac
- Borderlands 3 online not working
- Recent murders in fresno ca
- Big bang theory schedule tbs
These were the wonderful days of our youth, where there was a lot, both joyful and sad, friendship and quarrels, then again reconciliation. They helped each other as much as they could. To some extent, one could call it love, but then we did not understand it. No, it was not the kind of love that brings us all to bed and sex.
It was friendship in the highest degree of its manifestation, without parasitism on it.